Forklift Drive Motor - MCC's or likewise known as Motor Control Centersare an assembly of one or more sections that include a common power bus. These have been used in the automobile trade since the 1950's, for the reason that they were made use of a lot of electric motors. Nowadays, they are utilized in various industrial and commercial applications.
Inside factory assembly for motor starter; motor control centers are somewhat common practice. The MCC's include metering, variable frequency drives and programmable controllers. The MCC's are normally seen in the electrical service entrance for a building. Motor control centers frequently are utilized for low voltage, 3-phase alternating current motors that vary from 230 V to 600V. Medium voltage motor control centers are intended for large motors which vary from 2300 volts to 15000 volts. These units use vacuum contractors for switching with separate compartments in order to attain power switching and control.
Within factory area and locations that have corrosive or dusty processing, the MCC can be installed in climate controlled separated locations. Usually the MCC will be positioned on the factory floor adjacent to the machinery it is controlling.
A MCC has one or more vertical metal cabinet sections with power bus and provisions for plug-in mounting of individual motor controllers. Smaller controllers can be unplugged from the cabinet in order to complete maintenance or testing, whereas very large controllers can be bolted in place. Each and every motor controller has a solid state motor controller or a contractor, overload relays In order to protect the motor, fuses or circuit breakers so as to supply short-circuit protection as well as a disconnecting switch so as to isolate the motor circuit. Separate connectors enable 3-phase power to enter the controller. The motor is wired to terminals situated inside the controller. Motor control centers supply wire ways for power cables and field control.
Each and every motor controller in a motor control center can be specified with several choices. These choices consist of: separate control transformers, extra control terminal blocks, control switches, pilot lamps, and numerous types of solid-state and bi-metal overload protection relays. They even comprise various classes of types of power fuses and circuit breakers.
There are several alternatives regarding delivery of MCC's to the client. They could be delivered as an engineered assembly with interlocking wiring to a central control terminal panel board or programmable controller along with internal control. Conversely, they could be provided set for the customer to connect all field wiring.
Motor control centers normally sit on the floor and should have a fire-resistance rating. Fire stops can be necessary for cables that go through fire-rated walls and floors.
Click to Download the pdf